Redundant Power Supply Module GE Fanuc IC200MDL650 Input Micro Controller Control Module
Points IC200MDL640, BXIOIS1624: 16 (2 groups of 8)
IC200MDL650, BXIOID3224: 32 (4 groups of 8)
Module ID IC200MDL640, BXIOIS1624: FFFF8008
IC200MDL650, BXIOID3224: 80088008
User input to logic (optical) and frame ground: 250VAC
continuous; 1500VAC for 1 minute
Group to Group: 250VAC continuous; 1500VAC for 1 minute
Isolation: Point to point: None
LED indicators One LED per point shows individual point ON/OFF status
OK LED indicates backplane power is present
consumption (5V output)
IC200MDL640, BXIOIS1624: 25mA maximum
IC200MDL650, BXIOID3224: 50mA maximum
External power supply None
Thermal derating IC200MDL640, BXIOIS1624: No derating
IC200MDL650, BXIOID3224: See chart
Configurationparameters Input response times
Input voltage 0 to +30VDC,+24VDC nominal
On state voltage +15 to +30VDC
Off state voltage 0 to +5VDC
On state current 2.0 to 5.5mA
Off state current 0 to 0.5mA
On response time 0.5ms maximum
Off response time
Configurable filter time 0 ms, 1.0ms (default), or 7.0ms
Input impedance 10kOhms maximum
OTHER SUPERIOR PRODUCTS
|Yasakawa Motor, Driver SG-
|Mitsubishi Motor HC-,HA-
|Westinghouse Modules 1C-,5X-
|GE Modules IC -
|Fanuc motor A0-
|Yokogawa transmitter EJA-
Contact person: Anna
Discrete input modules IC200MDL640 and BXIOID1624 provide two groups of 8 discrete inputs.
Discrete input module IC200MDL650 (shown below) and BXIOIX3224 provide four groups of 8 discrete inputs.
Inputs in each group can be either positive logic inputs that receive current from input devices and return the current on the common, or negative-logic inputs that receive current from the common and return
current to the input device. Input devices are connected between the input terminals and common terminals.
Individual green LEDs indicate the on/off state of each input point. The green OK LED is on when backplane power is present to the module.
Carefully inspect all shipping containers for damage. If any equipment is damaged, notify the delivery service immediately. Save the damaged shipping container for inspection by the delivery service. After
unpacking the equipment, record all serial numbers. Save the shipping containers and packing material in case it is necessary to transport or ship any part of the system.
Installation in Hazardous Locations
• EQUIPMENT LABELED WITH REFERENCE TO CLASS I, GROUPS A, B, C & D, DIV. 2 HAZARDOUS LOCATIONS IS SUITABLE FOR USE IN CLASS I, DIVISION 2, GROUPS A, B,
C, D OR NON-HAZARDOUS LOCATIONS ONLY
• WARNING - EXPLOSION HAZARD - SUBSTITUTION OF COMPONENTS MAY IMPAIR SUITABILITY FOR CLASS I, DIVISION 2;
• WARNING - EXPLOSION HAZARD - WHEN IN HAZARDOUS LOCATIONS, TURN OFF POWER BEFORE REPLACING OR WIRING MODULES; AND
• WARNING - EXPLOSION HAZARD - DO NOT DISCONNECT EQUIPMENT UNLESS POWER HAS BEEN SWITCHED OFF OR THE AREA IS KNOWN TO BE NONHAZARDOUS.
No derating is required for the 16-point modules, or for the 32-point modules at 24VDC in any orientation.
For 32-point modules at 30VDC, the number of points that can be on at the same time depends on the ambient temperature, the external voltage, and the orientation of the module and DIN rail
Product Revision History
IC200MDL640G / BXIOID1624G
IC200MDL650G / BXIOID3224G
October 2008 Updated Power Supply OK
IC200MDL640F / BXIOID1624F
IC200MDL650F / BXIOID3224F
April 2005 Improvement to latching
April 2004 Changed to V0 plastic for
January 2004 Changed to V0 plastic for
module housing. ATEX
approval for Group 2
Category 3 applications.
January 2004 ATEX approval for Group 2
Category 3 applications.
IC200MDL640C / BXIOID1624C
IC200MDL650C / BXIOID3224C
November 1999 Added operation with
negative logic inputs.
IC200MDL640A / BXIOID1624A
IC200MDL650A / BXIOID3224A
September 1998 Origin
The 32 inputs form groups of 8. Each group has a common connection. Each group may be wired for positive or negative logic inputs. Note: Negative-logic functionality requires module version -C or higher.
For the 16-point modules, if additional bussed terminals are needed, the B terminals can be made available using a shorting bar. The shorting bar has a maximum current-carrying capacity of 2 Amps per point. See the VersaMax I/O Modules Manual, GFK-1504 for information about using a shorting bar.
Wiring Connections for Carriers with Two Rows of Terminals Row B connections shown below are for 32-point modules only
Wiring Connections for Carriers with Three Rows of Terminals Side B connections shown below are for 32-point modules only